Dear experts, Is this acceptable? Based on my observation there is Incomplete weld deposit. How about the orientation of the weldolet?
Branch weld connection determine to follow your project specification or construction code application.
Yes, we normally determined Tm “nominal thickness of the branch weld for integrally reinforced branch connection fittings”.
Refer to construction codes
ASME B31.1 - 2018
- 127.4.8 Welded Branch Connections
- Figure 127.4.8-5 Some Acceptable Details for Integrally Reinforced Outlet Fittings
ASME B31.3 - 2018
- Para. 328.5.4 - welded branch connections
- Figure 328.5.4F Acceptable Details for Integrally Reinforced Branch Connections
You may refer other topics: Welded Branch Connections or Determine thickness of groove weld type SET-ON/SET-IN nozzle.